Ex h IIC T6 Gb bzw. Ex h IIIC T80°C Db (EN 60079-0:2018 und EN ISO 80079-36:2017)
BVS 19 ATEX E 028 bzw. IECEx BVS 19.0033
A resistance of 106 Ω between mobile equipment, holding tanks and vehicles of the installations is sufficient to prevent a dangerously high charge. Before each operation, e.g. the opening of tanks, the connection of pipes or hoses for filling or emptying, the mobile equipment, tanks and vehicles shall be earthed by means of a potential equalization conductor so that the resistance between the equipment to be earthed and the potential equalization or, if applicable, a charge bridge is less than 106 Ω and, in practice, is reduced to low, single-digit values. The temporary equalizer connection must not be remo-ved until all operations have been completed.
CR7K cable length max. 10 m conducteur cross section standard 10 mm² (option 4 or 6 mm²)
CRXK cable length max. 25 m conducteur cross section standard 10 mm² (option 4 or 6 mm²)